Skip to code content (skip section selection)
A distribution box installed after the effective date of this chapter shall meet the following requirements:
(a) A distribution box shall be watertight and shall be constructed of the same materials authorized for construction of a septic tank. The inner surface of the distribution box shall be resistant to sewer gas corrosion.
(b) All outlets from a distribution box shall be at exactly the same elevation and shall be located at least two inches above the bottom of the box. The inlet to the distribution box shall be one inch above the elevation of the outlets.
(c) A distribution box shall be connected to an on-site wastewater treatment system.
(Amended by Ord. No. 3061 (N.S.), effective 5-11-67; amended by Ord. No. 6049 (N.S.), effective 6-11-81; amended by Ord. No. 9273 (N.S.), effective 12-15-00; amended by Ord. No. 10136 (N.S.), effective 4-15-11)