Skip to code content (skip section selection)
The building sewer shall be constructed of Extra Strength Clay Sewer Pipe and Fittings meeting the requirement of ASTM C-700 with polyurethane joints meeting the requirements of ASTM C-425; or Poly (Vinyl Chloride) (P.V.C.) Plastic Pipe and fittings meeting the requirements of ASTM D-3034 with joints meeting the requirements of ASTM D-1869. If installed in filled or unstable ground, the pipe shall be laid on a suitable improved bed or cradle as approved by the Superintendent. All joints shall be made in strict accordance with the manufacturer's recommendations.
(Ord. 1984-35, passed 12-18-84) Penalty, see § 51.999