Skip to code content (skip section selection)
Add Section B-907.2.3.1 as follows:
B-907.2.3.1 Occupant load of 50 or less. Where a manual fire alarm system is not provided in Group E occupancies with an occupant load of 50 or less, interconnected smoke alarms shall be installed in accordance with Section 907.2.10 and a minimum of one smoke alarm shall be installed in each classroom or child care room.
Delete Section 907.6.4.1 and replace as follows:
B-907.6.4.1 Zoning indicator panel. A zoning indicator panel and the associated controls shall be provided at a visible location at the main entrance of the building or other location approved by the Fire Department. The visual zone indication shall lock in until the system is reset and shall not be cancelled by the operation of an audible-alarm silencing switch.
Add Section B-919 as follows: