Skip to code content (skip section selection)
(A) The applicant and user shall be responsible for all new service expense from the water meter to the apartment, flat, place of business, or family unit, and for all maintenance after installation from the water meter to the apartment, flat, place of business, or family unit.
(B) Such service line must be at least five-eighths of an inch in diameter, must be installed at a minimum depth of 42 inches, must have a minimum working pressure rating of 160 psi at 73.4°F, and must be constructed of one of the following types of material: copper, type K, polyvinyl chloride (PVC), polyethylene, or polybutylene.
(C) The applicant or his or her agent shall not cover service lines until they are inspected and approved by a duly authorized village representative, and the applicant or his or her agent will not connect any service lines or other plumbing connected with the service line to any other water source.
(D) The service line must meet any requirements of the state’s Department of Public Health, in addition to all required in this chapter and other ordinances of the village.
(Prior Code, § 13.16.020) Penalty, see § 51.99