Skip to code content (skip section selection)
1. General. Every park shall contain an electrical wiring system consisting or wiring, fixtures, equipment and appurtenances which shall be installed and maintained in accordance with local electric power company’s specifications regulating such systems.
2. Power Distribution Lines.
A. All power lines shall be placed underground at least 18 inches below the ground surface and shall be insulated and specifically designed for such installa tion. Such lines shall be located not less than 1 foot distance from any other utility line, facility or installation.
B. Meter poles shall have a maximum height of 6 feet.
3. Individual Electrical Connections. Each mobile home lot shall be provided with an approved disconnecting device and over-current protective equipment. The minimum service per outlet shall 120/240 volts AC, 100 amperes.
4. Required Grounding. All exposed non-current-carrying metal parts of mobile homes and all other equipment shall be grounded by means of an approved grounding conductor run with branch circuit conductors or other approved method of grounded metallic wiring. The neutral conductor shall not be used as an equipment ground for the mobile home or other equipment.
(Ord. 6/6/1977, §908)