Skip to code content (skip section selection)
1. General. All mobile home parks shall connect to the public water supply system, and every mobile home, service building, and other accessory facilities shall
use water from the public system exclusively.
2. Individual Connections.
A. Individual water riser pipes having an inside diameter of no less than ½ inch shall be provided on each mobile home stand and shall terminate no less than 4 inches above the ground level.
B. Adequate provisions shall be made to prevent freezing of service lines, valves and riser pipes and to protect risers from heaving and thawing actions of ground during freezing weather.
C. A shut-off valve below the front line shall be provided near the water riser pipe on each mobile home lot.
(Ord. 6/6/1977, §906)