Skip to code content (skip section selection)
(A) Each water service applicant shall provide a main supply shutoff valve or valves, just inside the building foundation wall, along with all piping and appurtenances, installed and maintained by the applicant. All work and materials shall be subject to inspection and approval by any authorized inspector in accordance with the utility general rules and regulations and/or other regulatory agencies as applicable.
(B) (1) Each service connection of three- fourths inch in size, shall be fitted with a compression-type stop and waste valve on the inlet side of the meter.
(2) Each water service connection of one inch in size or larger shall be fitted with a gate or ball- type shut-off valve or valves on both the inlet and outlet side of the meter.
(C) Service lines of larger sizes and/or supplying special equipment may require special valving and fitting arrangements as specified in this chapter and elsewhere.
(Ord. 19-01, passed 4-9-19) Penalty, see § 52.999