Skip to code content (skip section selection)
A. The 2005 national electrical code published by the National Fire Protection Association is hereby adopted by reference as the electrical code of the village, except for such additions, insertions, deletions or changes as hereinafter prescribed in subsection B of this section.
B. The following are amendments to the electrical code:
Article 320 Armored Cable
Section 320.10 Uses Permitted. Delete the entire section after the section heading and replace with: Where necessary to pass wire through existing partitions, cable type "AC" may be used in the village of River Forest, and to extend not more than 3 feet beyond said partitions. All other uses are prohibited without special permission of the code official.
Article 334 Nonmetallic-Sheathed Cable. Delete this article in its entirety. Nonmetallic sheathed cable types "NM", "NMC", and "NMS" are not permitted to be used in the village of River Forest.
(Ord. 3239, 5-12-2008)