Skip to code content (skip section selection)
For all swimming pools:
A. The general layout of bathhouses shall be such that bathers leaving the dressing room pass the toilets and showers, in sequence, before entering the pool.
B. Separate dressing rooms shall be provided for each sex and equipped with baskets or other checking facilities adequate for the maximum number of people to be accommodated.
C. All entrances to and exits from the dressing rooms shall be effectively screened to interrupt the line of sight of persons outside the dressing rooms.
D. Walls and partitions of dressing rooms, locker rooms, toilets and showers shall be light-colored, smooth, nonabsorbent and easily cleanable. Concrete or pumice blocks used for interior wall construction in these locations shall be finished and sealed to provide an easily cleanable surface.
E. Floors shall be of nonslip construction, free of open cracks and sloped to adequate drains so that the surface will be free of standing water and puddles.
F. All furniture shall be of simple character and easily cleanable. Locker compartments, partitions, furniture, and other appurtenances to dressing rooms shall be so installed or raised above the floor to permit thorough cleaning and flushing down of the dressing rooms and bathhouse interior.
G. Hose bibbs shall be provided for flushing down the dressing rooms and bathhouse interior.
H. Dressing rooms, toilets and showers shall be provided with adequate lighting and ventilation.
I. Toilet facilities shall be provided for each sex in accordance with the following table:
One toilet for each one hundred bathers or fraction thereof.
One urinal for each one hundred bathers or fraction thereof.
One toilet for each fifty bathers or fraction thereof, but in no case shall less than two toilets be provided.
J. Shower and handwashing facilities with hot and cold or tempered water shall be provided for each sex in accordance with the following table. Tempered water only shall be provided at all shower heads. The water heater and thermostatic mixing valve shall be inaccessible to bathers and shall be capable of providing two gpm of ninety-degrees-Fahrenheit water to each head.
MEN OR WOMEN
One shower for each fifty bathers or fraction thereof.
One lavatory with mirror for each one hundred bathers or fraction thereof.
K. A supply of toilet paper shall be provided at all times.
(Ord. 1990-81 § 9, 1990: Ord. 1984-42 (part), 1984: prior code § 23.60.010(R))