Skip to code content (skip section selection)
8.3.3 Exemptions. The standards of this division 8.3.3 shall not apply to government-owned, operated, or maintained street lights located within a street right-of-way or other easement granted to the town.
(E) Maximum light levels. All outdoor lighting shall be designed and located such that the maximum illumination measured in foot candles at the property line shall not exceed one foot candle. The average intensity illumination for outdoor lighting shall not exceed an average of six foot candles in intensity as measured at grade. Vehicular use area lighting shall not exceed a maintained average of two and one-half foot candles.
(F) Hue. All outdoor and parking lot lighting fixtures, including: metal halide, mercury vapor, fluorescent, induction, white high-pressure sodium, and color-improved high-pressure sodium lamps used in non-cutoff fixtures shall be coated with an internal white frosting inside the outer lamp envelope.
(A) Wall-mounted lights shall be fully shielded luminaries (such as shoebox or can style fixtures) to prevent the light source from being visible from any adjacent residential property or public street right-of-way. Nothing in this division 8.3.5 shall prevent the use of decorative lighting fixtures provided that the source of illumination is not visible from adjacent lands used or zoned for residential purposes, and provided that the maximum illumination values comply with the standards in division 8.3.4(E), Maximum Light Levels.
(B) Wall packs on buildings may be used at entrances to a building to light unsafe areas. They are not intended to draw attention to the building or provide general building or site lighting. Wall packs on the exterior of the building shall be fully shielded (true cut-off type bulb or light source not visible from off-site) to direct the light downward and be of low wattage (preferably 100 watts or lower). Other accent lighting projected onto buildings may be allowed provided that it is approved through the site plan process.
8.3.6 Floodlights and spotlights. Floodlights and spotlights shall be selected, located, aimed, and shielded so that direct illumination is focused exclusively on a portion of the building facade or other intended site feature and away from adjoining lands or the right-of-way. On-site lighting may be used to accent architectural elements but shall not be used to illuminate entire portions of building(s). Such lighting shall be installed in a fixture that is shielded so that no portion of the light bulb extends below the bottom edge or above the top edge of the shield, and the main beam from the light source is not visible from adjacent lands or the adjacent right-of-way. Floodlights or other type of lighting attached to light poles that illuminate the site or building(s) are prohibited.
8.3.7 Illumination of outdoor sports fields and performance areas. All lighting fixtures serving outdoor sports fields and performance areas shall be equipped with a glare control package (e.g., louvers, shields, or similar devices), and the fixtures shall be aimed so that their beams are directed and fall within the primary playing or performance area.