Skip to code content (skip section selection)
The following amendments, additions, and deletions are hereby made to the 2018 International Residential Code for One-and Two-Family Dwellings, as adopted by this subchapter. Paragraph, section numbers refer to the 2018 International Residential Code for One-and Two-Family Dwellings numbering system. Code references not amended in this section shall be enforced as published in the reference document.
(A) Section R101.1 Title. Amend to read, "These provisions shall be known as the Residential Code for One- and Two-family Dwellings of the City of Yuma, and shall be cited as such and will be referred to herein as 'this code.'"
(B) Section R101.2 Scope. Add to end of Exception: "Subject to preemption by Arizona Revised Statutes, Title 9, Chapter 7, Article 1, Section 807, Mandated Sprinklers in Certain Residences Prohibited."
(C) Section R102.4 Referenced codes and standards. Add to end of section. "Where reference in this code is made to the International Fire Code, it shall be taken to mean the current adopted fire code."
(D) Section R103.1 Creation of enforcement agency. Amend to read, "The Department of Community Development, Building Safety Division, is hereby created and the official in charge thereof shall be known as the building official."
(E) Section R104.10.1 Flood hazard areas. Delete section in its entirety in favor of adopted City floodplain ordinances.
(F) Section R105.1 Required. Add to end of section, "In addition, Park Models, as defined in Chapter 2 of the Code, require a building permit for placement. Electrical connections that are hard-wired to the unit require a separate permit. Mechanical equipment that is external to the unit requires a separate permit. Tie-down anchors are required for park model installations as specified in Chapter 4."
(G) Section R105.2 Work exempt from permit. Add new items #11 and #12, under "Building":
11. "Window replacements of like size where framing is not altered and any required emergency egress dimensions are not diminished from existing.
12. Replacement of an existing electric water heater in the same location.
Items #11 and #12 apply only to work performed by a licensed contractor or the owner/occupant of the premises."
(H) "Section R105.10 Toilet facilities on construction sites. Toilet facilities shall be provided for construction workers and such facilities shall be maintained in a sanitary condition. Construction worker toilets of the non-sewer type shall conform to ANSI Z4.3.
Toilet facilities shall be required at a ratio of at least one toilet for a maximum of 15 lots under construction."
(I) "Section R105.11 Construction Debris. "Construction sites shall be kept reasonably clean of construction debris during the course of construction. Construction debris shall be removed or retained on the lot and not at risk to be displaced from the lot by wind. Debris shall not be allowed to transfer to adjacent lots or City rights-of- way.
If the Building Official determines that the construction site is not in compliance with this section or the debris presents a safety hazard for inspection personnel, inspections shall not be performed until the construction site is cleaned."
(J) Section R106.1.4 Information for construction in flood hazard areas. Delete item 4 in its entirety.
(K) Section R106.4 Amended Construction documents. Add to end of section, "Changes may be made without resubmittal that are not affecting code-related items, or when otherwise approved by the building official."
(L) Section R108.2 Schedule of permit fees. Amend by adding Building Permit Fee Table 1-A.
TABLE 1-A: BUILDING PERMIT FEES
Schedule of Building Permit Fees
$1 to $500
$501 to $2,000
$50.00 for the first $500 plus $4 for each additional $100, or fraction thereof, to and including $2,000
$2,001 to $25,000
$110.00 for the first $2,000 plus $16 for each additional $1,000, or fraction thereof, to and including $25,000
$25,001 to $50,000
$478.00 for the first $25,000 plus $12 for each additional $1,000, or fraction thereof, to and including $50,000
$50,001 to $100,000
$780.00 for the first $50,000 plus $8 for each additional $1,000, or fraction thereof, to and including $100,000
$100,001 to $500,000
$1,180.00 for the first $100,000 plus $6 for each additional $1,000, or fraction thereof, to and including $500,000
$500,001 to $1,000,000
$3,580.00 for the first $500,000 plus $6 for each additional $1,000, or fraction thereof, to and including $1,000,000
$1,000,001 and up
$6,580.00 for the first $1,000,000 plus $4 for each additional $1,000, or fraction thereof
Other Inspections and Fees:
1. Permit fees for mechanical, plumbing and electrical shall be as indicated per applicable fee tables of the respective ordinances.
2. Inspections outside of normal business hours, $50 per hour* (minimum charge - 2 hours)
3. Reinspection fees of $50 per hour*, for work not ready for inspection.
4. Inspections for weekends and holidays, $100 per hour* (minimum charge - 2 hours).
5. Inspection fees for which no fee is specifically indicated, $50 per hour* (minimum charge - one-half hour)
6. Additional plan review required by changes, additions or revisions to plans, $50 per hour* (minimum charge - one-half hour)
7. For use of outside consultant. For plan checking and inspections, or both Actual Costs**
* Or the total hourly cost to the jurisdiction, whichever is the greatest. This shall include supervision, hourly wages and fringe benefits of the employee involved.
** Actual costs include administrative and overhead costs.
(M) "Section R108.2.1 Plan review fees. When submittal documents are required by Section R106.1, a plan review fee shall be paid at the time of submitting the submittal documents for plan review. Said plan review fee shall be 65 percent of the building permit fee as shown in Table 1 -A.
The plan review fees specified in this section are separate fees from the permit fees specified in Section R 108.2 and are in addition to the permit fees.
When submittal documents are incomplete or changed so as to require additional plan review, an additional plan review fee shall be charged at the rate shown in Table 1-A."
(N) Section R108.5 Refunds. Amend to read, "The building official shall authorize the refunding of fees as follows:
1. The full amount of any fee paid hereunder that was erroneously paid or collected.
2. Not more than 80 percent of the permit fee paid when no work has been done under a permit issued in accordance with this code.
3. Not more than 80 percent of the plan review fee paid when an application for a permit for which a plan review fee has been paid is withdrawn or canceled before any plan review effort has been expended.
The building official shall not authorize the refunding of any fee paid except upon written application filed by the original permittee not later than 180 days after the date of fee payment."
(O) Section R108.6 Work commencing before permit issuance. Add to end of section, "An investigation fee, in addition to the permit fee, shall be collected whether or not a permit is then or subsequently issued. The investigation fee shall be determined by the building official, based on the circumstances, nature, and severity of the infraction. The minimum investigation fee shall be $50.00 and the maximum shall be an amount up to the same as the fee set forth in Table 1 -A."
(P) Section R109.4 Approval required. Add to end of section, "Inspection comments shall include code section references, when requested."
(Q) Section R110.3 Certificate issued. Amend to read, "After the building official inspects the building or structure and does not find violations of the provisions of this code or other laws that are enforced by the jurisdiction, the building official may issue a certificate of occupancy upon request, which shall contain the following:
1. The building permit number.
2. The address of the structure.
3. The name and address of the owner or the owner's authorized agent.
4. A description of that portion of the structure for which the certificate is issued.
5. A statement that the described portion of the structure has been inspected for compliance with the requirements of this code.
6. The name of the building official.
7. The edition of the code under which the permit was issued.
8. If an automatic sprinkler system is provided and whether the sprinkler system is required.
9. Any special stipulations and conditions of the building permit"
(R) Section R112.1 General. Add to end of section, "The membership of the Residential Advisory Board, as prescribed in Section 150-175 of the Yuma City Code, will be the Board of Appeals."
(S) Section R112.3 Qualifications. Delete section in its entirety.
(T) Section R113.4 Violation penalties. Amend to read, "Any person who violates a provision of this code or fails to comply with any of the requirements thereof or who erects, constructs, alters or repairs a building or structure in violation of the approved construction documents or directive of the building official, or of a permit or certificate issued under the provisions of this code, shall be subject to the penalty and fine described in this ordinance."
(U) Section R114.2 Unlawful continuance."Any person who shall continue any work in or about the structure after having been served with a stop work order, except such work as that person is directed to perform to remove a violation or unsafe condition, shall be subject to the penalty and fine described in this ordinance."
(V) CHAPTER 2 DEFINITIONS. "Park Model. Any factory assembled portable unit, to which is affixed an Arizona recreational vehicle seal, mounted on a chassis and wheels, not more than 12 feet in width and no greater than 400 square feet nor less than 320 square feet in total area, and permanently connected to utilities that are necessary for the operation of the installed park model with no holding tank."
(W) TABLE R301.2(1) CLIMATIC AND GEOGRAPHIC DESIGN CRITERIA.
Amend table to add values applicable to this jurisdiction:
CLIMATIC AND GEOGRAPHIC DESIGN CRITERIA
Ground Snow Load
Seismic Design Categoryf
Subject to Damage From
Winter Design Tempe
Ice Barrier Underlayment Requiredh
Air Freezing Indexi
Mean Annual Tempj
Speedd (mph )
Moderate to Heavy
1980, 1987, 2004, 2006
Manual J Design Criteria
Altitude Correction Factor
Indoor Design Temp
Design Temp Cooling
Heating Temp Diff
Cooling Temp Diff
Wind Velocity Heating
Wind Velocity Cooling
Coincident Wet Bulb
(X) Table R301.2(1) CLIMATIC AND GEOGRAPHIC DESIGN CRITERIA. Add to end of footnote f. "All locations in City of Yuma shall be classified as Seismic Design Category Do."
(Y) Section R301.2.2.6 Irregular buildings. Add exception to Item 6. Perpendicular shear wall and wall bracing. "Exception: Angled walls, per provisions of Section R602.10.1.4."
(Z) Section R302.1 Exterior walls. Add exceptions 6 and 7 to section:
6. "In mobile home parks and other applicable zoning districts,(such as MHS. MHP. RVS. RV Co-Op) that are existing at time of this code adoption, dwelling units and their attached accessory structures are permitted to maintain their prior avproved fire separation distance, subject to compliance with other City codes, but in no case shall the fire separation distance be less than 3 feet (914 mm), with unlimited unprotected openings, and no projections allowed.
7. For existing dwellings and other structures having legal, nonconforming setbacks at time of this code adoption, where approved by the zoning administrator and the building official, additions are permitted to comply with the existing nonconforming setbacks, provided the minimum fire separation distance is 3 feet (914 mm), with unlimited unprotected openings, and no projections allowed."
(AA) Section R304.1 Minimum area. Add to end of section. "Every dwelling unit shall have at least one habitable room that shall have not less than 120 square feet (11 m2) of gross floor area."
(BB) Create new section. "Section R304.4 Access from bedrooms. Bedrooms shall not constitute the only means of access to other bedrooms or habitable spaces and shall not serve as the only means of egress from other habitable spaces."
Exception: Units that contain fewer than two bedrooms.
(CC) Section R313.2 One- and two-family dwellings automatic fire systems. Delete section in its entirety. (Preemption by ARS § 9-807).
(DD) Section R313.2.1 Design and installation. Clarification: This section is to remain.
(EE) Section R317.3.1 Fasteners for preservative-treated wood. Add fourth exception to section:
4. "Fasteners for preservative-treated wood in areas not normally subjected to high moisture."
(FF) Section R318.1 Subterranean termite control methods. Add to end of section, "Method 3 or 4 shall be incorporated per Section R317.1, regardless of other methods or combination of methods utilized."
(GG) SECTION R322 FLOOD-RESISTANT CONSTRUCTION. Delete section in its entirety in favor of adopted City floodplain ordinances.
(HH) Section R324.2 Solar thermal systems. Amend to read, "Solar thermal systems shall be designed and installed in accordance with Chapter 23 and the current adopted fire code."
(II) Section R401.2 Requirements. Add to end of section, "Engineered fill building pads shall be placed in 12-inch lifts, compacted to not less than 95% Maximum Density, per ASTM D698 or D1557. The building pads shall extend a minimum of 3-feet beyond the footprint of the building at an elevation level not less than 10-inches below the finished floor.
Park Model installations shall be provided with tie-downs using approved manufactured housing tie-down anchors. As a minimum, tie-down anchors shall be installed at each corner of the unit and intermediately spaced at maximum 12 feet (3658 mm) on-center."
(JJ) Section R401.2 Requirements. Add exception to section:
"Exception: Fills depths 12-inches or less may not require testing subject to determination by the building official."
(KK) Section R403.1.2 Continuous footing in Seismic Design Categories D0, D1 and D2. Amend third sentence to read, "Required interior braced wall panels at buildings located in Seismic Design Categories D0, D1 and D2 shall be supported by continuous solid or fully grouted masonry or concrete footings in accordance with Section R403.1.3.4 at intervals not exceeding 60 feet (18288 mm) in both directions."
(LL) Section R403.1.3 Footing and stem wall reinforcing in Seismic Design Categories D0, D1 and D2. Add to end of section, "The reinforcing steel requirements of this section and subsections shall also be applicable in Seismic Design Category C for unincorporated areas in Yuma County."
(MM) Section R403.1.3.4 Interior bearing and braced wall panel footings in Seismic Design Categories D0, D1 and D2. Amend to read, "In Seismic Design Categories D0, D1 and D2, interior footings supporting bearing walls or braced wall panels with a foundation, and cast monolithicallv with a slab on grade, shall extend to a depth not less than 12 inches (305 mm) below the top of the slab."
(NN) Section R403.1.4 Minimum depth. Amend first sentence to read, "All exterior footings shall be placed at least 12 inches (305 mm) below the undisturbed ground surface, or 12 inches (305 mm) into engineered pad."
(OO) Section R403.1.6.1 Foundation anchorage in Seismic Design Categories C, D0, D1 and D2. Add item 7 to section:
7. "Interior braced wall panels when not supported by a continuous foundation shall be attached to the concrete slab on ground using ½ inch (12.7 mm) diameter anchor or expansion bolts spaced at not more than 6 feet (1829 mm) on center, or an equivalent method such as approved pneumatic anchor pins as per manufacturer requirements. Cut nails or adhesives shall not be permitted."
(PP) Section R408.7 Flood Resistance. Delete section in its entirety in favor of adopted City floodplain ordinances.
(QQ) Section R506.1 General. Add to end of section, "Control joints in unreinforced concrete slab-on-ground floors shall be provided at maximum 12 feet (3658 mm) on center in both directions."
(RR) Section R506.2.3 Vapor retarder. Amend section title to read, "Section R506.2.3 Vapor retarder (Optional)."
(SS) Section R602.10.1.3 Spacing of braced wall lines. Add exception to section:
"Exception: As an exception to braced wall line spacing of Table R602.10.1.3, in detached one- and two-story dwellings, for seismic bracing, spacing between braced wall lines may be up to 30 feet (9144 mm) x 45 feet (13716 mm) for one single room and one attached garage, each not exceeding 1,350 square feet (125.42m2) per dwelling unit. When this exception is taken all the following shall apply:
1.1 Wall bracing at braced wall lines surrounding the single room and one attached garage shall be Method WSP of Section R602.10.4.
1.2 Braced wall panel locations shall be as per Sections R602.10.2.2 and R602.10.2.2.1, and length of bracing provided as per Sections R602.10.3 and R602.10.5.
1.3 The entire length of braced wall lines surrounding the single room and garage shall be continuously sheathed with wood structural panel sheathing (WSP).
1.4 Braced wall panel locations at the single room and garage shall have a maximum 3 1/2:1 height-width ratio, except for methods ABW and PFH of Section R602.10.4.
1.5 Braced wall lines surrounding the single room and garage shall be supported by continuous foundations around the entire braced wall lines.
1.6 Spacing of all other interior braced wall lines shall not exceed 25 feet."
(TT) Section R602.10.2.2.1 Braced wall panel location in Seismic Design Categories D0, D1 and D2. Add exception 3 and 4 to section:
"3. Interior braced wall panels shall begin within 10 feet (3810 mm) from each end of a braced wall line as determined in Section R602.10.1.1.
4. For braced wall panel construction Method WSP of Section R602.10.4, the braced wall panel shall be permitted to begin no more than 12.5 feet (3810 mm) from each end of the braced wall line, where a designed collector is provided. See sketches SK1, SK2, and SK3 for designed collectors and applicable conditions."
(UU) Section R602.10.7 Ends of braced wall lines with continuous sheathing. Add exception to section:
"Exception: The first braced wall panel shall be permitted to begin 12.5 feet (3810 mm) from each end of the braced wall line in Seismic Design Category D0,where a designed collector is provided. See sketches SK1, SK2, and SK3 for designed collectors and applicable conditions."
(VV) Section R602.10.8 Braced wall panel connections. Add to end of section, "This section also applies for connections of interior braced wall panels to roof trusses and rafters."
(WW) TABLE R702.3.5 MINIMUM THICKNESS AND APPLICATION OF GYPSUM BOARD AND GYPSUM PANEL PRODUCTS. Amend last sentence of footnote "d" of table to read, "Where applying a water-based texture material, the minimum gypsum board thickness shall be increased from 3/8 inch to 1/2 inch for 16-inch on center framing."
(XX) Section N1101.16 (R401.3) Certificate (Mandatory). Amend section title to read, "N1101.14 (R401.3) Certificate (Optional)."
(YY) Section N1102.3 (R402.3) Fenestration (Prescriptive). Add exception to section:
"Exception: Standard insulated garage doors shall be permitted at conditioned garages and are not subject to the fenestration air leakage requirements of Section N1102.4.3. For use of this exception the garage conditioning shall be a dedicated mechanical system. Register/diffuser openings at the garage ceiling shall include ceiling radiation dampers or ducts shall be constructed of minimum No. 26 gage (0.48 mm) sheet steel."
(ZZ) Section N1102.4 (R402.4) Air Leakage (Mandatory). Add to end of section, "Building envelope air tightness and insulation installation shall be demonstrated to comply with one of the following options given by Section N118.104.22.168 or N122.214.171.124."
(AAA) Section N1126.96.36.199 (R402.4.1.2) Testing. Amend section title to read, "N1188.8.131.52 (R402.4.1.2) Testing option."
(BBB) "Section N1184.108.40.206 Visual inspection option. The components listed in Table N1220.127.116.11, applicable to the method of construction, are field verified. Where required by the building official, an approved party independent from the installer of the insulation, shall inspect the air barrier and insulation."
(CCC) Table N118.104.22.168 (R402.4.1.1) AIR BARRIER AND INSULATION INSTALLATION. Amend as follows:
a. "COMPONENT, 'Shower/tub on exterior wall.' Delete in its entirety.
b. COMPONENT, 'Electrical/phone box on exterior walls.' Delete in its entirety.
(DDD) Section N1103.5 (R403.5) Service hot water systems. Amend section title to read, "Service hot water systems (Optional)."
(EEE) Section N1103.5.1 (R403.5.1) Heated water circulation and temperature maintenance systems (Mandatory). Amend section title to read, "Heated water circulation and temperature maintenance systems (Optional)."
(FFF) Section N1103.6 (R403.6) Mechanical Ventilation. Amend to section title to read, "Section N1103.6 (R403.6) Mechanical ventilation (Optional)."
(GGG) Section N1103.10.3 (R403.10.3) Covers. Amend section title to read, "Section N1103.10.3 (R403.10.3) Covers (Optional)."
(HHH) Section N1103.12 (R403.12) Residential pools and permanent residential spas. Delete section in its entirety.
(III) Section N1104.1 (R404.1) Lighting equipment (Mandatory). Amend section title to read, "Section N1104.1 (R404.1) Lighting equipment (Optional)."
(JJJ) Section M1602.2 Return Air Openings. Amend Exception 5 to read:
"5. For other than dedicated HVAC systems, return air shall not be taken from indoor swimming pool enclosures and associated deck areas."
(KKK) Section G2406.2 (303.3) Prohibited locations. Delete items 3 and 4 in their entirety.
(LLL) Section G2407.5 (304.5) Indoor combustion air. Add to beginning of section, "Indoor combustion air shall not be used in new construction within the building envelope. Garages of minimum 400 square feet in area may use combination of infiltration and partial exterior combustion air for one standard water heater fuel gas appliance up to 50,000 Btu/h total input capacity."
(MMM) Section G2407.7 (304.7) Combination indoor and outdoor combustion air. Add to beginning of section, "Combination indoor and outdoor combustion air shall not be used in new construction within the building envelope. Garages of minimum 400 square feet in area may use combination of infiltration and partial exterior combustion air for one standard water heater fuel gas appliance up to 50,000 Btu/h total input capacity."
(NNN) Section G2413.2 (402.2) Maximum gas demand. Add to end of section. "Where an input rating is not indicated, the gas supplier, appliance manufacturer or a qualified agency shall be contacted, or the rating from Table G2413.2 may be used for estimating the volumetric flow of gas to be supplied.
TABLE G2413.2 (R402.2)
APPROXIMATE GAS INPUT FOR TYPICAL APPLIANCES
Input BTU/M (Approx. )
Space Heating Units
Multifamily, per unit
Multifamily, per unit
Space and Water Heating Units
Multifamily, per unit
Water Heating Appliances
Water heater, automatic instantaneous
Capacity at 2 gal/minute
Capacity at 4 gal/minute
Capacity at 6 gal/minute
Water heater, automatic storage, 30 to 40 gal tank
Water heater, automatic storage, 50 gal tank
Water heater, domestic circulating or side-arm
Built-in oven or broiler unit, domestic
Built-in top unit, domestic
Range, free standing, domestic
Clothes dryer, Type 1 (domestic)
Gas fireplace, direct- vent
(OOO) Section G2414.5.3 (403.5.3) Copper or copper-alloy tubing. Add to end of section, "Copper or copper-alloy tubing shall not be used in natural gas piping systems, due to hydrogen sulfide content which cannot be guaranteed to be delivered from the serving utility provider to meet the code acceptable levels."
(PPP) Section G2415.12 (404.12) Minimum burial depth. Amend to read, "Underground piping systems shall be installed a minimum depth of 12 inches (305 mm) below grade."
(QQQ) Section G2415.12.1 (404.12.1) Individual outdoor appliances. Delete section in its entirety.
(RRR) Section G2415.17.1 (404.17.1) Limitations. Amend exception 3 to read:
"3. Plastic pipe shall be permitted under uncovered outdoor patio, walkway and driveway slabs provided that the burial depth complies with Section G2415.12."
(SSS) TABLE G2422.214.171.124 (503.10.2.4) MINIMUM THICKNESS FOR GALVANIZED STEEL VENT CONNECTORS FOR LOW-HEAT APPLIANCES.
"0.019 inch 28 Ga.
0.023 inch 26 Ga.
0.029 inch 24 Ga.
0.034 inch 22 Ga.
0.056 inch 18 Ga."
(TTT) Section G2445.4 (621.4) Prohibited Locations. Add to end of section, "Unvented room heaters shall not be installed in bedrooms or bathrooms."
(UUU) Section P2503.4 Building sewer testing. Delete section in its entirety.
(VVV) Section P2503.5.2 Finished plumbing. Delete item 2 in its entirety.
(WWW) Section P2603.5.1 Sewer depth."Building sewers that connect to private sewage disposal systems shall be at not less than 12 inches (305 mm) below finished grade at the point of septic tank connection. Building sewers shall be not less than 12 inches (305 mm) below grade."
(XXX) Section P2804.6.1 Requirements for discharge pipe. Amend Item #5 to read:
"5. Discharge to the floor of the garage (where the garage floor is sloped and below the floor level of the dwelling), to a waste receptor or to the outdoors."
(YYY) Section P2902.5.3 Lawn irrigation systems. Rename section/title to read "Section P2902.5.3 Landscape irrigation systems." Add to beginning of section. "A landscape irrigation system shall be provided for all new dwellings, consisting of a stub-out, electric valve (or valves) and backflow protection."
(ZZZ) Section P2904.1 General. Add item #5 to end of section:
"5. The system is integral with the domestic water piping system. See Section P2902.5.4 for protection of separate/independent sprinkler piping systems."
(AAAA) Section P2906.5 Water-distribution pipe. Add to end of section, "Use of copper at inaccessible water piping under slabs shall be limited to Type K, with no joints."
(BBBB) Section E3406.3 Minimum size of conductors. Amend first sentence to read, "The minimum size of conductors for feeders and branch circuits shall be 12 AWG copper and 1 AWG aluminum or copper-clad aluminum for current carrying conductors (shall not apply for grounding conductor)."
(CCCC) Section E3601.1 Scope. Add to end of section, "Local utility company installation regulations may exceed/supersede installation requirements of this chapter."
(DDDD) Section E3604.2.2 Vertical clearance from grade. In item 1, amend 10 feet (3048 mm) to 12 feet 6 inches (3810 mm). In item 2, amend 12 feet (3658 mm) to 12 feet 6 inches (3810 mm).
(EEEE) Section E3607.3.2 Grounded conductor, existing premises. Add exception to section:
"Exception: If the Load Center or Panel Board does not have provisions for a Main Disconnect and an approved fastening method, a permanent placard shall be installed on the Main Service to indicate the location of the detached Panel on the property. The over current protective device shall also have a lock-out device installed."
(FFFF) TABLE E3702.14 (Table 210.24) BRANCH-CIRCUIT REQUIREMENTS-SUMMARY. Amend table to delete 14 AWG conductors.
(GGGG) Section E3901.12 HVAC outlet. Amend exception to read:
"Exception: A receptacle outlet shall not be required for the servicing of evaporative coolers or rooftop HVAC equipment."
(HHHH) Section E3902.2 Garage and accessory building receptacles. Add exception to section:
"Exception: GFCI protection shall not be required for single receptacle outlets dedicated for a specific use (such as a freezer) and single receptacle outlets for garage door openers."
(Ord. O2001-74, passed 9-19-01; Ord. O2005-49, passed 7-20-05; Ord. O2007-22, passed 4-18-07; Ord. O2007-30, passed 5-16-07; Ord. O2013-11, passed 4-3-13; Ord. O2013-54, passed 10-16-13; Ord. O2018-051, passed 12-5-18)