Skip to code content (skip section selection)
(A) All buildings shall have a readily accessible, visible external shutoff valve located on the building for liquid or vapor fuels.
(B) All vents for combustible fuel appliances shall terminate a minimum of 35 inches above final grade.
(C) Flexible gas line connectors shall not be permitted for furnace and water heater installations.
(D) Corrugated stainless steel tubing shall not be permitted in any application.
(E) Fire dampers, where required, shall be accessible for periodic inspection by qualified personnel.
(Ord. 14-103, passed 5-15-2014) Penalty, see § 150.999