Skip to code content (skip section selection)
The following sections of the International Plumbing Code, 2015 Edition are hereby revised as follows:
In all chapters and sections, where "name of jurisdiction" and/or "chief appointing authority of the jurisdiction" is written, insert "City of Sycamore."
101.2 Scope - Amended as follows: The provisions of the International Plumbing Code shall apply only to Chapter 11 Storm Drainage and Section 403.3.2 Prohibited toilet room location - "Toilet rooms shall not open directly into a room used for the preparation of food for service to the public."
The following shall be added to Chapter 11 - Storm Drainage:
1101.2.1 WINDOW WELL AND AREAWAY DRAINS - No window well or areaway drains shall be connected to the sanitary sewer system.
1104.2.1 FLOOR DRAINS - All interior floor drains shall be connected to the sanitary sewer system.
1105.3 DOWNSPOUTS - All downspouts or roof drains shall discharge onto the ground or be connected to storm sewer. No downspouts or roof drains shall be connected to the sanitary sewers.
1112.1.1 FOOTING DRAINS - Footing drains shall be connected to sump pump receptors and sump pump discharge shall be made into storm sewers by approved underground piping when storm sewers are available on the property. When storm sewers are not available on the property, discharge may be upon the ground to a drain swale or ditch. No footing drain discharge shall be upon a public way or into the sanitary sewer system.
1113.1.5 SUMP PUMPS - Sump shall be used for one function only, either the discharge of stormwaters or the discharge of sanitary sewage.
(Ord. 2019.20, 9-16-2019, eff. 1-1-2020)