Skip to code content (skip section selection)
Pursuant to the UCC, delete Section E3901.7 and replace as follows:
R-E3901.7 Outdoor outlets. At least one receptacle outlet that is accessible while standing at grade level and located not more than 6 feet, 6 inches (1981 mm) above grade, shall be installed outdoors at the front and back of each dwelling unit having direct access to grade. Balconies, decks, and porches that are accessible from inside of the dwelling unit and that have a usable area of 20 square feet (1.86 m 2) or greater shall have at least one receptacle outlet installed within the perimeter of the balcony, deck, or porch. The receptacle shall be located not more than 6 feet, 6 inches (1981 mm) above the balcony, deck, or porch surface.
Pursuant to the UCC, delete Section E3901.11 and replace as follows:
R-E3901.11 Foyers. Foyers that are not part of a hallway in accordance with Section E3901.10 and that have an area that is greater than 60 square feet (5.57 m 2) shall have a receptacle(s) located in each wall space that is 6 feet (1829 mm) or more in width, but a minimum of one receptacle. Doorways, door-side windows that extend to the floor, and similar openings shall not be considered as wall space.