Skip to code content (skip section selection)
P-708.1.1 Horizontal drains and building drains. Horizontal drainage pipes in buildings shall have cleanouts located at intervals of not more than 10050 feet (30 48015 240 mm) for lines four inch in diameter or less. Building drains shall have cleanouts located at intervals of not more than 100 feet (30 480 mm) for lines five inch in diameter and above. except where manholes are used instead of cleanouts, the manholes shall be located at intervals of not more than 400200 feet (12261 m). The interval length shall be measured from the cleanout ormanhole opening, along the developed length of the piping to the next drainage fitting providing access for cleaning, the end of the horizontal drain or the end of the building drain.
Exception: Horizontal fixture drain piping serving a nonremovable trap shall not be required to have a cleanout for the section of piping between the trap and the vent connection for such trap.
* * *