Skip to code content (skip section selection)
B-920.1 Fire hydrants. 287 Fire hydrants installed on private property shall be located and installed in accordance with Section F-507.5 of the Philadelphia Fire Code and as directed by the Fire Department. Hydrants shall be Philadelphia Standard as specified by the Water Department. Hydrants shall not be installed on a water main less than 6 inches (152 mm) in diameter.
Enrolled bill numbered this as B-916.1; renumbered as B-920.1 by Code editor.