Skip to code content (skip section selection)
Each water service pipe shall be of Type K copper pipe, shall be connected with the main water pipe, shall extend horizontally at right angles from such main water pipe to a point at least twenty-five feet from the centerline of the street, and shall be provided with a brass stopcock, of not less than three-fourths of an inch in diameter, to be installed within a telescopic shut-off box of the best quality of cast iron or first-grade steel pipe.
(Ord. 1987-41a. Passed 8-24-87.)