Skip to code content (skip section selection)
(A) New mobile home parks shall have an approved fire protection water supply system. The system shall include water mains, hydrants and appurtenances capable of providing a minimum of 500 gpm with 20 psi residual pressure at any hydrant on said system. Approved hydrants shall be installed so that every lot or structure in a mobile home park is within five hundred (500) feet of a hydrant. Materials and equipment used must meet the standards, rules and regulations of the most current edition of the Standard Specifications for Sewer and Water Construction in Wisconsin.
Note: Wisconsin DNR requires 500-gpm minimum at hydrants on fire protection water systems.
(B) All mobile home parks will install (at their expense) a sampling station suitable to the City of Medford Water Utility's needs and standards.
(Ord. 753, passed 5-5-98) Penalty, see § 9.4.99