Skip to code content (skip section selection)
(A) Lighting or other electrical circuits provided in the spray pad area must be protected by ground-fault circuit interrupters in accordance with the Uniform Code.
(B) Defects in the electrical system, including overhead lights and their respective lenses, shall be immediately repaired.
(C) Portable electrical devices, such as announcing systems and radios within the reach of patrons on the spray pad, shall be prohibited.
(D) When night use of the spray pad is permitted, surface lighting shall be adequate to allow an observer to clearly see the spray pad and deck.
(E) No overhead electrical wiring shall pass within 20 feet horizontally of the spray pad.
(Ord. 15, passed 8-5-08) Penalty, see § 92.99