Skip to code content (skip section selection)
(A) Plans for fire alarm systems, water-based fire protection systems, fire pumps, special hazard fire suppression systems, high-piled storage arrangements, and firestop systems shall be submitted to the Town Fire Department prior to the request for a required wall rough inspection.
(B) Each respective submittal shall contain the following information:
(1) Sprinkler systems:
(a) One full set of sprinkler/standpipe plans;
(b) One full set of sprinkler/standpipe calculations;
(c) One copy of the sprinkler construction design release (CDR); and
(d) One set of manufacturer’s cut-sheets for all sprinkler heads in the design.
(2) Fire alarm systems:
(a) One full set of fire alarm plans (one-eighth inch to one inch scale);
(b) One set of battery calculations;
(c) One copy of the fire alarm construction design release (CDR);
(d) One set of manufacturer’s cut-sheets for the fire alarm control panel (FACP) and fire alarm components; and
(e) One fire alarm performance matrix.
(3) Special hazard fire protection systems:
(a) One set of plans (if applicable);
(b) One set of engineering data (if applicable);
(c) One copy of the construction design release (if applicable); and
(d) One set of manufacturer’s cut-sheets for system components.
(4) Fire pumps:
(a) One copy of the manufacturer’s fire pump specifications; and
(b) One copy of the manufacturer’s certified pump test characteristic curve.
(5) Firestop systems:
(a) Through-penetration firestop systems;
(b) Membrane-penetration firestop systems;
(c) Fire-resistant joint systems;
(d) Perimeter fire barrier systems; and
(e) Fire-rated duct and air-transfer openings.