Skip to code content (skip section selection)
(A) Where a booster pump has been installed on the service line to or within any premises, such pump shall be equipped with a low pressure cut-off device designed to shut-off the booster pump when the pressure in the service line on the suction side of the pump drops to 20 psi or less.
(B) It shall be the duty of the water consumer to maintain the low pressure cut-off device in proper working order and to certify to the Code Enforcement Officer, at least once a year, that the device is operable.
(2000 Code, § 54.31) (Ord. 2433, passed 4-8-1997)