Skip to code content (skip section selection)
(A) All towers regulated by this chapter shall be grounded by ground wire installation which shall be approved by the code enforcement officer, which shall be No. 8 solid copper wire securely attached to 3/4-inch ground pipe, such ground pipe to be driven into the ground not less than 8 feet.
(B) The guy wires provided for in this chapter shall be not less than 6-strand No. 19 rust-resisting of a type approved by the code enforcement officer.
('64 Code, §§ 29-6, 29-7; amend. Ord. 7158, passed 11-19-85)