Skip to code content (skip section selection)
A. Adoption: The International Fuel Gas Code, 2015 edition, as published by the International Code Council, Inc. (ICC), is hereby adopted and incorporated by reference as part of this Code as if fully set forth herein, as part of the Building Code for the Village. The International Fuel Gas Code shall apply to the design construction, alteration, enlargement, equipment, repair, demolition, removal, conversion, and use of all buildings and structures except for single-family and two-family residences not over two (2) stories and an attic in height.
B. Amendments To International Fuel Gas Code: The International Fuel Gas Code as heretofore adopted is revised and amended as follows:
Section 101.1 Title. - Insert: "Village of Clarendon Hills"
Section 106.6.2 Fee Schedule. - Replace the section in its entirety with the following: "The fees for work shall be as indicated in the appropriate schedules in the village code."
Section 106.6.3 Fee Refunds. - Delete entire section.
Section 109 Means Of Appeal. - Delete entire section.
Section [M]306.3 Appliances In Attics. - Add new subsection [M]306.3.2 as follows:
"[M]306.3.2 Enclosure And Venting. Heat producing appliances installed in attic spaces shall be enclosed within a room sheathed with 5/8 inch drywall that provides adequate access and space for maintenance and allows sufficient intake of combustion air. The door shall be a 13/8" thick solid core wood or 20 minute fire rated door, with an automatic closer."
Section 403.4.4 Aluminum. Replace the section in its entirety with the following: "Aluminum-alloy pipe shall not be used."
Section 403.5.2 Copper And Copper Alloy Tubing. Replace the section in its entirety with the following: "Copper and brass tubing shall not be used."
Section 403.5.3 Aluminum Tubing. Replace the section in its entirety with the following: "Aluminum-alloy tubing shall not be used."
Section 404.9 Minimum Burial Depth. - Substitute the phrase "18 inches (457 mm)" for the phrase "12 inches (305 mm)".
Section 621.1 Unvented Room Heaters. - General. Replace the section in its entirety with the following: "Unvented room heaters are not permitted."
C. Copies On File: One copy of the International Fuel Gas Code shall be kept available in the Community Development Department at the Village Hall, for use, inspection and examination. (Ord. 18-12-27)